The Shadows Company est désormais compatible avec l'extension FastNews.kiwi disponible pour votre navigateur. Avec cette extension, vérifiez s'il y a des nouveaux sujets sur ce forum en un clic depuis n'importe quelle page !Cliquez ici pour en savoir plus.
NZS 2293.2:1995 Emergency Evacuation Lighting For Buildings ....pdf
b68026692e Where manual discharge test facility is present, operate the test switch and/or circuit breaker to simulate a power failure. Any corrective action must also be taken to repair faulty emergency lighting The names of the persons responsible for carrying out the maintenance work and the date the work was completed The logbook or alternative record system shall be kept on the premises at all times, or at such other locations as may be approved by the regulatory authority Who can carry out inspection & testing of electrical equipment? A licensed technician is required to carry out Emergency Lighting Testing & Inspection Your Next Steps: So that we can best assist you and your business with your compliance needs, please contact us on 1300 038 847 or 0417 188 505 and ask to speak to Tracy. Requirements apply to the Overview: Cross References: Catalog: File Format:PDF(Acrobat Reader) or Word version doc Document File Size:895KB Get More Infomation: Tile in English:emergency evacuation lighting for buildings - inspection and maintenance Comment No. HEALTH PROTECTION. 1 (2006/R2012) Mi.SANS 50934-1 Ed. Freestd Home >> Standards Wordwide >> Australia Standards(AS) >> AS/NZS 2293.2-1995 emergency evacuation lighting for buildings - inspection and maintenance .
Standards Worldwide DIN JSA-JIS IEEE ISO AS NF IEC EN GOST GME GMW CSA AFNOR GB UNI CECC KS IS SS ISUZU UIC ICAO UTE BOCA DELPHI SASO JEDEC JASO SNV DANSK SABS IETF VDI LST CODEX AOAC SFS CNS SNZ More. Twelve Monthly Procedures Carry out all checks as per six-monthly procedures. 2.04 (2014) Aggreg.SANS 50450-1 Ed. . 403 Forbidden. 1# Post time 2010-10-14 12:04:54 Show the author posts only Descending Read mode AS/NZS 2293.2:1995 Emergency evacuation lighting for buildings Part 2: Inspection and maintenance REMEMBER TO DELETE MARKS IN YOUR DOCUMENTS FIRST IT'S REALLY IMPORTANT FOR OUR MATERIALS IN FUTURE READ CAREFULLY: 2293, Emergency, lighting, 2293, Emergency, lighting, 2293, Emergency, lighting, 2293, Emergency, lighting This post contains more resources You have to Login for download or view attachment(s). What legislation applies? Australian Standard AS/NZS 2293.2:1995 states that Exit and Emergency lighting must be tested in accordance to the procedures described in clauses 3.2.2 and 3.2.3, and not exceed intervals of no greater than specified, which is 6 & 12 months.